The Honeywell UDC Universal Digital Controller is a microprocessor-based stand alone controller. It combines the highest degree of functionality and. Find great deals for Honeywell UDC Universal Digital Controller. Shop with confidence on eBay!. There are UDC ‘s at both ends, however as the set point is managed by Lookout, the controllers just provide local control and display the.
|Country:||Turks & Caicos Islands|
|Published (Last):||16 April 2008|
|PDF File Size:||18.16 Mb|
|ePub File Size:||13.75 Mb|
|Price:||Free* [*Free Regsitration Required]|
SPHiLim honeyweol the parameter that determines how high the setpoint on the controller can be wound up to. If you’re not already a member, consider joining. Select the categories for which you would like to see messages displayed By Chris Jenerick on 14 November, – Welcome to the Modbus Community, about the world’s leading automation protocol.
The set point should be honeysell desired level of the reservoir. Some tips for better search results Try those and reply if its still not working. By Anonymous on 23 July, – Put the controller in manual and wind the output up and down while watching the measured value.
Perhaps you could order one from Honeywell. The bound manual you are looking for is Product E.
Honeywell UDC 3000 Universal Digital Controller
So that i can help you to resolve the problem. By Darren on 15 November, – 4: What I hooneywell to identify is the value that drives the output. Your subscription request is being processed. I’ve fiddled around with a few UDCs and being typical Honeywell the book is about as clear and thick as mud. You have clicked on the “?
Note that common words and, that, etc. It doesnt limit the controller output as the PID function will wind the output up until saturation if the measured value never reaches the setpoint. Here are is the model number and settings. Adjust the head gate position to maintain reservoir level. You must be a Control. Inlet Flow and Outlet Flow. Could this be a span problem?
I would verify your getting yoneywell good uoneywell signal and the full range of gate movement in reponse.
Once you verify everything going in and out of the controller as it should I would then start to look at parameters INSIDE the controller. Hi Patti The bound manual you are looking for is Product E.
Honeywell UDC3000 Specification
Remember me on this computer. By Steve Smoker on 4 October, – 7: The UDC configuration described is a level control honeywe,l the object of the control loop appears to be:. First mention your complete model no. I would like a little more clarification on what your measuring and what your controlling – ‘gate position’ is pretty hard to measure unless you have some sort of valve positioner arrangement.
Since both UDC work to maintain level, there may be conditions where the two work together or against each other to maintain the reservoir level. Use double quotes around phrases, as follows: The outlet control is likely configured for direct operation increased level increase output, open gate.
You have given some good problem definition. The inlet control is likely configured for reverse operation increaed level decrease honeywelll, close gate.
HONEYWELL UDC SPECIFICATION Pdf Download.
To exclude a word, precede it with a “-“, as follows: It’s free, and you can customize the content you view, as well as being able to subscribe to threads and topics, getting new posts delivered to your email as they appear. The lake receives water from a river and releases it to the same down stream. The UDC configuration described is a level control wherein the object of the control loop appears to be: By Bill Clemons on 15 July, – 5: To search the site, enter your search terms in the box labeled “search the site” and hit Enter.
Please read those terms and conditions carefully. Please log in and try again. The output signal goes to the head gate and adjusts its position to increase or decrease flow into or out of the reservoir.
The UDC 300 also receive a level signal from the field indicating actual level. Username Password Remember me on this computer. The ‘Rng1’ error your getting refers to the analogue input UDC’s are twin-loop controllers though in your application loop 2 is disabled It shows that error when the input range goes above 20ma or 300 4ma.
NandaKumar on 16 July, – 8: